Check the motor winding resistance or ohms reading using a multimeter or ohmmeter for phase to phase terminal ( U to V,V to W ,W to U ). The ohms reading for each winding must be the same (or nearly the same). Remember that the three phases have identical windings or nearly so!
How do I know if my 3 phase motor is bad?
Using a multimeter, check the continuity of motor winding from phase to phase ( U to V, V to W , W to U ). Each phase to phase must have a continuity if winding is OK. If any particular phase fails the continuity test, your motor is probably burnt.
How do you know if a 3 phase motor is bad?
Check all three wires singly T1,T2,T3 (all three phases) to the ground wire. Readings should be infinite. If its zero or reads any continuity at all, then a problem exists with either the motor or cable . If it is go directly to the motor and disconnect from cable and check motor and the cable separately.
What is a bad insulation resistance reading?
The purpose of the IR test is to check for damaged insulation, this can be mechanical damage or damage by heat, (overloaded cables), readings less than 2 Mohm indicate damaged insulation, readings of 2-50 Mohm are indicative of long circuit lengths, moisture and contamination and do not indicate the insulation quality, …
What is the minimum insulation resistance of a motor?
It is recommended that the insulation resistance of the motor should at least be 1 MΩ1）, and for the voltage to ground of 200 V, I0r should be 200 μA or below.
What is a good Meg reading on a motor?
Our minimum meg readings are 1.5 megs for 480 volt motors at 1000 volt meg. (That would be 1.5 million ohms to ground resistance.) 1.5 to 20 is fair. 20 to 50 is good.
How many ohms should a 3 phase motor have?
The reading should be between 0.3 to 2 ohms. If it is 0, there is a short. If it is over 2 ohms or infinite, there is an open. You can also dry the connector and retest to possibly get more accurate results.
What is the resistance of a 3 phase motor?
Most are between 3 and 2.0 ohms. There are 8ohms. A short between phases exists if you read zero.
What is a bad reading on a megger?
What is a bad Megger reading? If the megger reads a resistance under 1 (1,000 ohms) on your meter after the initial 60-second interval, the cable has failed and the cable should be removed. If the megger reads a resistance between 1-1.25 on your meter, then the cable passes.
How do you perform a megger test?
Clamp the alligator clip on one of the megger probes to the wire or cable, touch the other probe to the exposed conductor and press the test button. The megger will generate a current between the probes, and the meter will record the resistance of the jacket to the flow of the current.